Western Heating & Air proudly provides air conditioning, heating and indoor air quality services to the residents of Bluffdale, UT. Our family owned and operated business is ready to provide you with professional expert HVAC services. We offer exceptional repair, installation and maintenance services on ACs, furnaces and HVACs.
With over 25 years in business, we are happy to serve you! We invite you to read some of our reviews below and find out why your neighbors consider us to be their nearby heating and air company Bluffdale, UT.
for Bluffdale, UT
Our Reviews by City
Dalton - Bluffdale, UT
Even though our unit wasn’t running well and was difficult to maintenance, our technician did a great job with what he had to work with.
Response from Western Heating & Air Conditioning (Lehi):
Hi Dalton, thank you so much for giving Jeff a 5 star review!
Julie - Bluffdale, UT
Very great customer service!
Call for Magic-Pak having a hard time keeping up. Checked temperature split and itâ€™s on coming out at a 15 degree temperature split ideally it should be falling between 18-22 degrees. No restrictions in the air flow observed itâ€™s believed there may be issues with refrigerant charge but with the way the unit is set up the service ports and gauges being placed on while unit is running is next to impossible to do. Canâ€™t accurately check pressures to say for absolute thereâ€™s a problem with it, itâ€™s just suspected given temperature split. Capacitor and electrical are measuring within manufacturer specifications, condenser fan has some sign of oil leaking indicating the gasket keeping the bearings sealed has failed and is leaking right now everything is all right with it but once the bearings dry up it will cause problems for the motor. Magic-Pakâ€™s parts are difficult to get when all is said and done if they do give up completely so be mindful of that. At this point system is co
Turn up on two York air-conditioning systems. Equipment is in overall good condition. I did notice a high static pressure in the supply duct which is typical of a damper system, As well possibly closed supply vents. I would recommend keeping vents open to reduce static pressure and reduce load and increase efficiency of air conditioning system. All of the electrical components are operating properly at this time.
Compressor I grounded customer has lost power to home because power is crossed inside the compressor. Customer will reach out to home warranty to see if they will cover the cost otherwise Western will provdie the service to the customer
System still has short which is causing all of these problems. System is running when I left.
Drain was leaking into where wet switch was. Fixed drain. System up and going when I left.
Furnace repair Lennox
Day and night AC repair
Ac tuneup on a York ac and replaced the filter