Western Heating & Air is a locally owned and family operated HVAC company serving the residents of West Valley City, UT and the surrounding areas. We offer exceptional repair, replacement and tune-up services on HVACs, furnaces and air conditioners. Our team is friendly and our technicians highly trained and certified.
We are happy to be your one-stop-shop for home comfort services! Check out some of our reviews below to find out why your neighbors choose to partner with us on their heating and cooling concerns in West Valley City, UT.
for West Valley City, UT
Our Reviews by City
" Great Service and Awesome customer service too "
Mia - West Valley City, UT
Customer service were so friendly and easy to talk to. I had same Technician before, he always so polite and explains well.
Call for poor cooling from previously installed equipment. Replaced filter with provided filter and tested air flow total External Static is very high sitting at a .90 inWC total when ideally it should fall closer to .50-.65 inWC. A few thing as to why this is the case is ultimately we do not have quite enough return making it to the system we have a total of two returns and the west most return doesnâ€™t feel like itâ€™s pulling quite enough from it so a majority of our airflow is trying to be pulled through the return in the hallway total return pressure is .47 inWC and ideally this should be sitting closer to .05-.15 inWC for maximum return. The main return drop is large enough for that much air but it would appear our horizontal runs are too small and we have inadequate amount of return air registers throughout the home. Existing ductwork is main culprit behind poor performance from equipment. Options of adding return will need to be considered.
They did not want to turn in the swamp cooler. They want central ac added. Mark is coming out at 2pm to give estimate.
Quarterly filter Change out. 3 of the 4 systems are working great. The 4th is still having some overheating issues. I adjusted the airflow again. It seems to be working better than it has in the past. We will keep an eye on it in future visits.
AC service call, Air conditioning repair
Lennox Ac not operating properly. Replaced dual run capacitor
Tempstart furnace clean up blower wheel
Finished furnace tune up on trane unit